<?xml version="1.0" encoding="UTF-8"?>
<!--Copyright (C) 2004-2015 InsBud www.insbud.net-->

<Device xmlns="http://www.insbud.net/common/devcfg" 
        xmlns:xsi="http://www.w3.org/2001/XMLSchema-instance"
        xsi:schemaLocation="http://www.insbud.net/common/devcfg devcfg.xsd"
        Version="1.2"
        HardwareId="1014" 
        FirmwareId="1" 
        FirmwareVersion="0">

    <!-- 
        plik konfiguracyjny pompy ciepła (KAISAI; MIDEA; SEVRA; NETSU itp)

        dla aplikacji ibvunit-2.0

        niniejszy plik konfiguracyjny został opracowany na podstawie dokumentacji rejestrów dostarczonej przez
        producenta.

        fabryczne parametry komunikacji: 9600/8-N-1 ID16

        ustawienie ID:

        przełącznik obrotowy S3

        The rotating coded switch S3(0-F) on the main control board of hydraulic module is used for set the modbus address.
        By default the units have this coded switch positioned=0, but this corresponds to the modbus address 16 , while the
        others positions corresponds the number, e.g. pos=2 is address 2, pos=5 is address 5.

    -->
        
  <!-- <HoldingRegisters SetMode="Single"> -->
  <HoldingRegisters>

    <!--
        Power on or off
         ▪ bit 0: 0: power off air conditioner; 1: power on air conditioner; (zone 1) (room temperature control)
         ▪ bit 1: 0: power off floor heating; 1: power on floor heating;(zone 1) (water flow temperature control)
         ▪ bit 2: 0: DHW(T5S) power off; 1: DHW(T5S) power on
         ▪ bit 3: 0: power off floor heating; 1: power on floor heating;(zone 2) (water flow temperature control)
    -->
    <HReg Addr="0" Name="power.on.off" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Setting the mode
         ▪ 0:Auto
         ▪ 1:Cool
         ▪ 2:Heat
    -->
    <HReg Addr="1" Name="mode" Rd="1" Wr="1" Min="0" Max="65535"  Presentation="unsigned"/>

    <!--
        Setting water water temperature T1S

        Bit0-Bit7 - Water temperature T1s is corresponding to the floor heating.(zone 1)
        Bit8-Bit15 - Water temperature T1s is corresponding to the floor heating.(zone 2)
    -->
    <HReg Addr="2" Name="setting.t1s" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Setting air temperature Ts

        The room temperature range is between 17°C and 30°C, and is valid when there is Ta.
        Portocol value=actual value*2

        In cooling mode, T1S low temp setting range is 5~25°C;T1S high temp setting range is 18~25°C.
        In heating mode, T1S low temp setting range is 22~55°C;T1S high temp setting range is 35~70°C.
    -->
    <HReg Addr="3" Name="setting.ts" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T5s

        The water tank temperature range is between 20°C and 75°C.
    -->
    <HReg Addr="4" Name="setting.t5s" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Function Setting

         ▪ bit 4: Disinfect
         ▪ bit 5: Holiday away (the status can only be read, but cannot be changed)
         ▪ bit 6: Silent mode
         ▪ bit 7: 0: Silent mode level1; 1: Silent mode level2
         ▪ bit 8: Holiday home (the status can only be read, not changed)
         ▪ bit 10: ECO mode
         ▪ bit 11: DHW pump's running constant-temperature water recycling
         ▪ bit 12: 1: climate curve setting is valid; 0: climate curve setting is invalid. (zone1)
         ▪ bit 13: 1: climate curve setting is valid; 0: climate curve setting is invalid. (zone2)
    -->
    <HReg Addr="5" Name="function.setting" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Curve selection

        Bit8-Bit15 - Climate Curve 1-9(zone 2)
        Bit0-Bit7 - Climate Curve 1-9(zone 1)
    -->
    <HReg Addr="6" Name="curve.selection" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Forced water heating

        0: Invalid
        1: Forced on
        2: Forced off

        TBH is the electric water tank heater.
        IBH1 and 2 are the hydraulic module's rear electric heater.
        IBH1 and 2 can be activated together.
        TBH cannot be activated together with IBH1 and IBH2.
    -->
    <HReg Addr="7" Name="forced.water.heating" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Forced TBH

        0: Invalid
        1: Forced on
        2: Forced off
    -->
    <HReg Addr="8" Name="forced.tbh" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Forced IBH1

        0: Invalid
        1: Forced on
        2: Forced off
    -->
    <HReg Addr="9" Name="forced.ibh" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_SG_MAX

        0-24 Hours
    -->
    <HReg Addr="10" Name="t_SG_MAX" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Operating frequency

        Compressor operating frequency in Hz
    -->
    <HReg Addr="100" Name="operating.frequency" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Operating Mode

        Outdoor unit's actual operating mode, 2: cooling, 3: heating, 0: off
    -->
    <HReg Addr="101" Name="operating.mode" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Fan Speed [r/min]
        
    -->
    <HReg Addr="102" Name="fan.speed" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        PMV openness

        Openness of the outdoor unit's electronic expansion valve in P
    -->
    <HReg Addr="103" Name="PMV.openness" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Water inlet temperature TW_in, unit: °C
    -->
    <HReg Addr="104" Name="TW_in" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Water outlet temperature TW_out, unit: °C
    -->
    <HReg Addr="105" Name="TW_out" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T3 Temperature

        Condenser temperature, unit: °C
    -->
    <HReg Addr="106" Name="T3" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4 Temperature

        Outdoor ambient temperature unit: °C
    -->
    <HReg Addr="107" Name="T4" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Discharge temperature

        Compressor discharge temperature Tp unit: °C
    -->
    <HReg Addr="108" Name="discharge.temperature" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Return air temperature

        Compressor air return temperature unit: °C
    -->
    <HReg Addr="109" Name="return.air.temperature" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1

        Total water outlet temperature unit: °C
    -->
    <HReg Addr="110" Name="T1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1B

        System total water outlet temperature (behind the auxiliary heater) , unit: °C
    -->
    <HReg Addr="111" Name="T1B" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T2

        Refrigerant liquid side temperature, unit: °C
    -->
    <HReg Addr="112" Name="T2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T2B

        Refrigerant gas side temperature, unit: °C
    -->
    <HReg Addr="113" Name="T2B" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Ta

        Room temperature, unit: °C
    -->
    <HReg Addr="114" Name="Ta" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T5

        Water tank temperature, unit: °C
    -->
    <HReg Addr="115" Name="T5" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Pressure 1

        Outdoor unit high pressure value, unit: kPa
    -->
    <HReg Addr="116" Name="pressure.1" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Pressure 2

        Outdoor unit low pressure value, unit: kPa
    -->
    <HReg Addr="117" Name="pressure.2" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Outdoor unit current

        Outdoor unit operating current, unit: A
    -->
    <HReg Addr="118" Name="outdoor.unit.current" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Outdoor unit voltage

        Outdoor unit voltage, unit: V
    -->
    <HReg Addr="119" Name="outdoor.unit.voltage" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Tbt1

        Tbt1, unit: °C
    -->
    <HReg Addr="120" Name="Tbt1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Tbt2

        Tbt2, unit: °C
    -->
    <HReg Addr="121" Name="Tbt2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Compressor operation time

        Compressor operating time in hour
    -->
    <HReg Addr="122" Name="compressor.operation.time" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Unit capacity

        0702 for 200 register is reserved. When it is 071x, data 4-30 means 4-30kW
    -->
    <HReg Addr="123" Name="unit.capacity" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Current fault

        Check the code table for detailed fault codes
    -->
    <HReg Addr="124" Name="fault.current" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Fault 1

        Check the code table for detailed fault codes.
    -->
    <HReg Addr="125" Name="fault.1" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Fault 2

        Check the code table for detailed fault codes.
    -->
    <HReg Addr="126" Name="fault.2" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Fault 3

        Check the code table for detailed fault codes.
    -->
    <HReg Addr="127" Name="fault.3" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Status bit 1

         ▪ bit 1: Defrosting
         ▪ bit 2: Anti-freezing
         ▪ bit 3: Oil return
         ▪ bit 4: Remote On/Off (1: d8)
         ▪ bit 5: Outdoor unit test mode mark
         ▪ bit 6: Heating mode set by room thermostat
         ▪ bit 7: Cooling mode set by room thermostat
         ▪ bit 8: Solar energy signal input
         ▪ bit 9: Anti-freezing operation for water tank
         ▪ bit 10: SG 1: normal electricity; 0: high price electricity (judge when EUV is 0)
         ▪ bit 11: EUV 1: free electricity; 0: judge by SG's signal
         ▪ bit 13: Request to send SN code, 1: request; 0: not request
         ▪ bit 14: Request to send software version, 1: request; 0: not request
         ▪ bit 15: Request to send operation parameter, 1: request; 0: not request
    -->
    <HReg Addr="128" Name="status.bit.1" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Load output

         ▪ bit 0: Electric heater IBH1
         ▪ bit 1: Electric heater IBH2
         ▪ bit 2: Electric heater TBH
         ▪ bit 3: Water pump PUMP_I
         ▪ bit 4: SV1
         ▪ bit 5: SV2
         ▪ bit 6: External water pump P_o
         ▪ bit 7: Water return water P_d
         ▪ bit 8: Mixed water pump P_c
         ▪ bit 9: SV3
         ▪ bit 10: HEAT4
         ▪ bit 11: Solar water pump
         ▪ bit 12: ALARM
         ▪ bit 13: RUN
         ▪ bit 14: Auxiliary heat source
         ▪ bit 15: DEFROST
    -->
    <HReg Addr="129" Name="load.output" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Software version

        1~99 is the software version of hydronic module
    -->
    <HReg Addr="130" Name="software.version" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Wired controller version No.

        1~99 is the wired controller's version number.
    -->
    <HReg Addr="131" Name="wired.controller.version" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Unit target frequency

        Hz
    -->
    <HReg Addr="132" Name="unit.target.frequency" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        DC bus current

        Unit: A
    -->
    <HReg Addr="133" Name="dc.bus.current" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        DC bus voltage

        The actual value/10, unit: V
    -->
    <HReg Addr="134" Name="dc.bus.voltage" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        TF module temperature

        Feedback on outdoor unit, unit: °C
    -->
    <HReg Addr="135" Name="tf.module.temperature" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Climate curve T1S calculated value 1

        The corresponding calculated T1S of zone 1
    -->
    <HReg Addr="136" Name="climate.curve.t1s.calculated.value.1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Climate curve T1S calculated value 2

        The corresponding calculated T1S of zone 2
    -->
    <HReg Addr="137" Name="climate.curve.t1s.calculated.value.2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Water flow

        The actual value*100, unit: m3/H
    -->
    <HReg Addr="138" Name="water.flow" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Limit scheme of outdoor unit current

        Scheme value
    -->
    <HReg Addr="139" Name="limit.scheme.of.outdoor.unit.current" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Ability of Hydraulic module

        The actual value*100, unit: kW
    -->
    <HReg Addr="140" Name="ability.of.hydraulic.module" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Tsolar

        
    -->
    <HReg Addr="141" Name="tsolar" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Quantity of units in parallel

        BIT1-BIT15 - Respectively represent the online status of slaves unit 1-15
    -->
    <HReg Addr="142" Name="quantity.of.units.in.parallel" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Higher bits for electricity consumption

        
    -->
    <HReg Addr="143" Name="electricity.consumption.hi" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Lower bits for electricity consumption

        
    -->
    <HReg Addr="144" Name="electricity.consumption.lo" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Higher bits for power output

        
    -->
    <HReg Addr="145" Name="power.output.hi" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Lower bits for power output

        
    -->
    <HReg Addr="146" Name="power.output.lo" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Home appliance type

        The upper 8 bits are the types of home appliances:
        Air to water heat pump: 0x07
        The middle 4 bits are product codes: 0x1*
        The lower 4 bits are sub-type: R32: 0x*2
    -->
    <HReg Addr="200" Name="home.appliance.type" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Temperature upper limit of T1S cooling

        Lower 8 bits are for zone 1. higher 8 bits are for zone 2
    -->
    <HReg Addr="201" Name="temperature.upper.limit.of.t1s.cooling" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature lower limit of T1S cooling

        Lower 8 bits are for zone 1. higher 8 bits are for zone 2
    -->
    <HReg Addr="202" Name="temperature.lower.limit.of.t1s.cooling" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature upper limit of T1S heating

        
    -->
    <HReg Addr="203" Name="temperature.upper.limit.of.t1s.heating" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature lower limit of T1S heating

        
    -->
    <HReg Addr="204" Name="temperature.lower.limit.of.t1s.heating" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature upper limit of TS setting

        Protocol value = actual value * 2
    -->
    <HReg Addr="205" Name="temperature.upper.limit.of.ts.setting" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature lower limit of TS setting

        Protocol value = actual value * 2
    -->
    <HReg Addr="206" Name="temperature.lower.limit.of.ts.setting" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature upper limit of water heating

        
    -->
    <HReg Addr="207" Name="temperature.upper.limit.of.water.heating" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        Temperature lower limit of water heating

        
    -->
    <HReg Addr="208" Name="temperature.lower.limit.of.water.heating" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        PUMP RUNNING TIME

        DHW PUMP water return running time. It is five minutes by
        default and can be adjusted between 5 and 120 min at an interval
        of 1 min.
    -->
    <HReg Addr="209" Name="pump.running.time" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Parameter setting 1

         ▪ bit 0: 0: room cooling/heating first, 1: water heating first
         ▪ bit 1: Dual Room Thermostat, 0: not supported;1: supported
         ▪ bit 2: Room thermostat
         ▪ bit 3: Supports room thermostat
         ▪ bit 4: Supports room temperature Sensor Ta
         ▪ bit 5: PUMPI silent mode, 1; valid, 0: invalid
         ▪ bit 6: T1S heating high/low temperature settings(Read-only)
         ▪ bit 7: Enable heating
         ▪ bit 8: T1S cooling high/low temperature settings(Read-only)
         ▪ bit 9: Enable cooling
         ▪ bit 10: DHW pump is valid in disinfection mode
         ▪ bit 12: DHW PUMP, 1: supported; 0: not supported
         ▪ bit 13: Supports disinfection
         ▪ bit 14: Supports water tank electric heater TBH(Read-only)
         ▪ bit 15: Enable water heating
    -->
    <HReg Addr="210" Name="parameter.setting.1" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        Parameter setting 2

         ▪ bit 0: IBH/AHS installation position 1: buffer tank 0: pipe
         ▪ bit 1: Tbt sensor enable1: Yes 0: No
         ▪ bit 2: Ta sensor position 1: IDU 0: HMI
         ▪ bit 3: Double zone setting is valid
         ▪ bit 4: Setting the high/low temperature of heating mode T1S
         ▪ bit 5: Setting the high/low temperature of cooling mode T1S
         ▪ bit 6: T1B sensor enable 0: None 1: Yes
         ▪ bit 7: Smart grid, 0=NON; 1=YES
         ▪ bit 8: Define the port, 0=remote ON/OFF; 1=DHW heater
         ▪ bit 9: Solar energy kit enable 1: Yes 0: No
         ▪ bit 10: Solar energy input port 1: CN18 0: CN11
         ▪ bit 11: Piping length selection 1: >10m 0: <10m
         ▪ bit 12: Tbt2 sensor is valid 1: Yes 0: No
         ▪ bit 13: RT_Ta_PCNEn(enable Temperature Collection Kit) 1: Yes 0: No
         ▪ bit 14: M1M2 is used for AHS control 1: Yes 0: No
         ▪ bit 15: Reserved, wrong address is reported whe n this register is queried
    -->
    <HReg Addr="211" Name="parameter.setting.2" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        dT5_On

        Default setting: 10°C, range: 1~30°C;
    -->
    <HReg Addr="212" Name="dt5_on" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        dT1S5

        Default setting: 10°C, range: 5~40°C, setting interval: 1°C
    -->
    <HReg Addr="213" Name="dt1s5" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T_Interval_DHW

        Default setting: 5 min, range: 5~30 min, setting interval: 1 min
    -->
    <HReg Addr="214" Name="t_interval_dhw" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T4DHWmax

        Default setting: 43°C, range: 35~43°C, setting interval: 1°C
    -->
    <HReg Addr="215" Name="t4dhwmax" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4DHWmin

        Default: -10°C, range: -25~30°C;
    -->
    <HReg Addr="216" Name="t4dhwmin" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        t_TBH_delay

        Default setting: 30 min, range: 0~240 min, setting interval: 5 min
    -->
    <HReg Addr="217" Name="t_tbh_delay" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        dT5S_TBH_off

        Default setting: 5°C, range: 0~10°C, setting interval: 1°C
    -->
    <HReg Addr="218" Name="dt5s_tbh_off" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4_TBH_on

        Default setting: 5°C, range: -5~50°C;
    -->
    <HReg Addr="219" Name="t4_tbh_on" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T5s_DI

        Temperature for the disinfection operation, range: 60~70 ° C, default setting: 65°C
    -->
    <HReg Addr="220" Name="t5s_di" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        t_DI_max

        Maximum disinfection duration, range: 90~300 min, default setting: 210 min
    -->
    <HReg Addr="221" Name="t_di_max" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_DI_hightemp

        Disinfection high temperature duration, range: 5~60 min, default setting: 15 min
    -->
    <HReg Addr="222" Name="t_di_hightemp" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_interval_C

        Time interval of compressor start-up in cooling mode; range: 5~30 min, default setting: 5 min
    -->
    <HReg Addr="223" Name="t_interval_c" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        dT1SC

        Default setting: 5°C, range: 2~10°C, setting interval: 1°C
    -->
    <HReg Addr="224" Name="dt1sc" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        dTSC

        Default setting: 2°C, range: 1~10°C, setting interval: 1°C
    -->
    <HReg Addr="225" Name="dtsc" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4cmax

        Default setting: 43°C, range: 35~46°C, setting interval: 1°C
    -->
    <HReg Addr="226" Name="t4cmax" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4cmin

        Default setting: 10°C, range: -5~25°C, setting interval: 1°C
    -->
    <HReg Addr="227" Name="t4cmin" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        t_interval_H

        Time interval of compressor start-up in the heating mode; range: 5~60 min, default setting: 5 min
    -->
    <HReg Addr="228" Name="t_interval_h" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        dT1SH

        Default setting: 5°C, range: 2-20°C;
    -->
    <HReg Addr="229" Name="dt1sh" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        dTSH

        Default setting: 2°C, range: 1~10°C, setting interval: 1°C
    -->
    <HReg Addr="230" Name="dtsh" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4hmax

        Default setting: 25°C, range: 20~35°C, setting interval: 1°C
    -->
    <HReg Addr="231" Name="t4hmax" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4hmin

        Default setting: -15°C, range: -25-30°C, Setting interval 1°C
    -->
    <HReg Addr="232" Name="t4hmin" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4_IBH_on

        Ambient temperature for enabling the hydraulic module auxiliary
        electric heating IBH, range: -15~10°C; default setting: -5°C
    -->
    <HReg Addr="233" Name="t4_ibh_on" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        dT1_IBH_on

        Temperature return difference for enabling the hydraulic module auxiliary
    -->
    <HReg Addr="234" Name="dt1_ibh_on" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        t_IBH_delay

        Delay time of enabling the hydraulic module auxiliary electric heating IBH
    -->
    <HReg Addr="235" Name="t_ibh_delay" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T4_AHS_on

        The trigger ambient temperature for turning on AHS
    -->
    <HReg Addr="237" Name="t4_ahs_on" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        dT1_AHS_on

        The temperature difference between the heat pump ’ s leaving water set temperature (T1S) and the heat
    -->
    <HReg Addr="238" Name="dt1_ahs_on" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_AHS_delay

        Delay time for enabling the external heater AHS, range: 5~120 min;
        default setting: 30 min
    -->
    <HReg Addr="240" Name="t_ahs_delay" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_DHWHP_max

        Longest duration of water heating by the heat pump, range:
        10~600 min, default setting: 120 min;
    -->
    <HReg Addr="241" Name="t_dhwhp_max" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_DHWHP_restrict

        Duration of limited water heating by the heat pump, range: 10~600 min, default setting: 30 min;
    -->
    <HReg Addr="242" Name="t_dhwhp_restrict" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T4autocmin

        Default setting: 25°C, range: 20~29°C, setting interval: 1°C
    -->
    <HReg Addr="243" Name="t4autocmin" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4autohmax

        Default setting: 17°C, range: 10~17°C, setting interval: 1°C
    -->
    <HReg Addr="244" Name="t4autohmax" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1S_H.A_H

        Default setting: 25°C, range: 20~29°C, setting interval: 1°C
    -->
    <HReg Addr="245" Name="t1a_h.a_h" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T5S_H.A_DHW

        In the holiday mode, setting of T1 in the water heating mode, range: 20~25°C, default setting: 25°C
    -->
    <HReg Addr="246" Name="t5s_h.a_dhw" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        PER_START ratio

        Range10-100, default setting10.Setting interval10
    -->
    <HReg Addr="247" Name="per_start.ratio" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        TIME_ADJUST

        Range1-60 default setting5
    -->
    <HReg Addr="248" Name="time_adjust" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        dTbt2

        Rrange0-50 default setting15
    -->
    <HReg Addr="249" Name="dtbt2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        IBH1 power

        Range0-200, default setting0, unit: 100W
    -->
    <HReg Addr="250" Name="ibh1.power" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        IBH2 power

        Range0-200, default setting0, unit: 100W
    -->
    <HReg Addr="251" Name="ibh2.power" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        TBH power

        Range0-200, default setting0,unit: 100W
    -->
    <HReg Addr="252" Name="tbh.power" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_DRYUP

        Temperature rise day number, range: 4~15 days, default setting: 8 days
    -->
    <HReg Addr="255" Name="t_dryup" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_HIGHPEAK

        Drying day number, range: 3~7 days, default setting: 5 days
    -->
    <HReg Addr="256" Name="t_highpeak" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        t_DRYD

        Temperature drop day number, range: 4~15 days, default setting: 5 days
    -->
    <HReg Addr="257" Name="t_dryd" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T_DRYPEAK

        Highest drying temperature, range: 30~55°C, default setting: 45°C
    -->
    <HReg Addr="258" Name="t_drypeak" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        t_firstFH

        Running time of floor heating for the first time, default setting: 72 hrs, range: 48-96 hrs
    -->
    <HReg Addr="259" Name="t_firstfh" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T1S (first floor heating)

        T1S of floor heating for the first time, range: 25~35 ° C, default setting: 25°C
    -->
    <HReg Addr="260" Name="t1s.first.floor.heating" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1SetC1

        Parameter of the ninth temperature curves for cooling mode, range: 5~25°C, default setting: 10°C
    -->
    <HReg Addr="261" Name="t1setc1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1SetC2

        Parameter of the ninth temperature curves for cooling mode, range: 5~25°C, default setting: 16°C
    -->
    <HReg Addr="262" Name="t1setc2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4C1

        Parameter of the ninth temperature curves for cooling mode, range: (-5) ~46°C, default setting: 35°C
    -->
    <HReg Addr="263" Name="t4c1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4C2

        Parameter of the ninth temperature curves for cooling mode, range: (-5) ~46°C, default setting: 25°C
    -->
    <HReg Addr="264" Name="t4c2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1SetH1

        Parameter of the ninth temperature curves for cooling mode, range: 25~65°C, default setting: 35°C
    -->
    <HReg Addr="265" Name="t1seth1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T1SetH2

        Parameter of the ninth temperature curves for cooling mode, range: 25~65°C, default setting: 28°C
    -->
    <HReg Addr="266" Name="t1seth2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4H1

        Parameter of the ninth temperature curves for cooling mode, range: (-25) ~30°C, default setting: -5°C
    -->
    <HReg Addr="267" Name="t4h1" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        T4H2

        Parameter of the ninth temperature curves for cooling mode, range: (-25) ~30°C, default setting: 7°C
    -->
    <HReg Addr="268" Name="t4h2" Rd="1" Wr="1" Min="-32766" Max="32766" Presentation="signed"/>

    <!--
        

        The type of power input limitation, 0=NON, 1~8=type 1~8, default: 0
    -->
    <HReg Addr="269" Name="type.of.power.input.limitation" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        HB: t_T4_FRESH_C: Range: 0.5~6 hour, setting interval: 0.5 hour, sending value=actural value*2
        LB: t_T4_FRESH_H: Range: 0.5~6 hour, setting interval: 0.5 hour, sending value=actural value*2
    -->
    <HReg Addr="270" Name="t_t4_fresh" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        T_PUMPI_DELAY

        Range: 0.5~20 hour, setting interval: 0.5 hour, sending value=actural value*2
    -->
    <HReg Addr="271" Name="t_pumpi_delay" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>

    <!--
        EMISSION TYPE

        Bit0-3: The type of zone 1 end for heating mode
        Bit4-7: The type of zone 2 end for heating mode
        Bit8-11: The type of zone 1 end for cooling mode
        Bit12-15: The type of zone 2 end for cooling mode
    -->
    <HReg Addr="272" Name="emission.type" Rd="1" Wr="1" Min="0" Max="65535" Presentation="unsigned"/>


    <!--
    <HReg Addr="" Name="" Rd="1" Wr="0" Min="-32766" Max="32766" Presentation="signed"/>
    -->


  </HoldingRegisters>

  <InputRegisters>

  </InputRegisters>
  
  <Coils>

  </Coils>
  
  <DiscreteInputs>

  </DiscreteInputs>


</Device>